Our qualified technicians performed a RUUD air conditioner repair in Miami, Florida. The customer called on saying that their AC constantly overloaded. Fuse specialists arrived and ran a diagnostic. It turned out that parts of the electrical line didn’t match the Amper range at the condenser. The working range of the condenser is 40 Amp and the breaker was set to 20 Amp and 60 Amp fuses. Our techs replaced the breaker with the 40 Amp breaker and set the fuses for 40 Amp. After the repair the AC started working perfectly fine again.